This article describes the reason and gives a work around when the values on BACnet or Modbus doesn´t change.
- Intesis KNX Protocol Translators: (IN701KNX1000000, IN701KNX2500000, IN701KNX6000000, IN701KNX1K20000, IN701KNX3K00000).
When trying to map objects in Intesis MAPS, it may happen that you do not see any updates on the BACnet or Modbus side, however you have changed the values on the KNX side.
POSSIBLE CAUSES / ANSWER
There might be these missing flags (U and W) to get the correct status, which is marked in red square in the MAPS image below:
U, the object can be updated from KNX after power failure.
W, the object can be written from KNX.
To know more about how to use our Intesis MAPS, check our Intesis MAPS eLearning